Press the MANUAL ON button one time to override the schedule and set the zone to occupied for the amount of time defined in the Each pulse field on the RS sensor microblock’s Properties page in WebCTRL. Press the button again to incrementally increase the time. For example, if the Each pulse field is set at five minutes, press the button once for an occupancy of five minutes, twice for ten minutes, and so on. The maximum length of time you can override the schedule is defined in the Max Accum field on the Properties page. The display shows the duration of the override in minutes. If the override time exceeds 199 minutes, the display shows the time in hours. To cancel the override, hold the button down until 0 displays. Wait five seconds for the display to show the current zone temperature again.
West Michigan Environmental Action Council
1007 Lake Dr. SE
Grand Rapids MI 49506
Tel: (616) 451-3051
Fax: (616) 451-3054